Pleasant climatic conditions are the basic condition for the efficiency of the persons working in the cleanroom, as they are already impaired by their cleanroom clothing. It must also always be ensured that the employees do not begin to sweat due to excessive room temperatures.
Heat dissipation in summer is usually more energy-intensive that heating in winter. Heat loads in the cleanroom are waste process heat, lighting, persons and solar radiation, which should be prevented wherever possible via external shading.
The cooling output depends on the quantity of cooled air and the permissible undertemperature, which should not exceed 6 K.
- Air density (average value 1.2)
- Mass flow of air
- Specific heat capacity of air
- Cooling capacity of air
Please complete the red fields.
DisclaimerThe calculation tools of bc-technology GmbH merely represent an orientation and planning aid for cleanroom users.
No responsibility is accepted for the completeness of the information of this page .
The content and structure of these calculation tools are protected by copyright. Reproduction of information or data, in particular the use of texts, extracts of texts, formulae or parts of formulae require previous permission.